23 Jun Relationship with other publications This revision of BS takes into sites – Code of practice BS +A, Requirements For. 5 Sep Earthing standards. Installation of a well designed earthing system is BS Code of practice for protective earthing of electrical. BS EN Earthing of power installations exceeding 1kVac. – BS Code of practice for protective earthing of electrical installations. – BS Code of.
|Published (Last):||27 February 2011|
|PDF File Size:||16.45 Mb|
|ePub File Size:||4.6 Mb|
|Price:||Free* [*Free Regsitration Required]|
The resistivity found applies to soil depth a, so by repeating the measurement with different values of athe average resistivity to various depths may be found and the results indicates whether any advantage is to be gained by installing deeply driven electrodes in order to reach strata of a lower resistivity. It is important to ensure that their resistance areas do not overlap.
Measurements and Calculations Of Earth Electrode Systems (BS ) | EEP
The basic nature and properties of soil in a given location cannot be changed without considerable expense, and careful consideration of the geology should be used to determine the best location for an earthing system. It is essential to measure the resistance to earth of any metalwork it is intended to use as an electrode, and to monitor its value at regular intervals afterwardsin order to confirm that it continues to provide an adequate connection to earth.
It is of particular relevance to: To obtain a low overall resistance the current density should be as low as possible in the medium surrounding the electrode. System earthing involves the provision of a connection to the general mass of earth. First published bs 7430 code of practice for earthing CP This is related to the hemispherical radius of the rod and that has avoided the effects of using less than the two-times constraint in design thinking. It is important bs 7430 code of practice for earthing consideration is given to the possibility of corrosion of the metalwork reinforcement.
Facebook Linkedin Google Plus Twitter. Earthing systems should consist of copper conductors, copper clad or austenitic steel rods of appropriate dimensions, cast iron plates, or steel piles used individually or connected together in combination to form a single local earth electrode system.
Where the structure is supported on many similar footings, it bs 7430 code of practice for earthing be considered feasible and more satisfactory to measure the resistance of one footing before it is electrically connected to othersand before there are any other electrically paralleled footings close by.
This is lower than some types of soil. Document Status Indicators The Green document status indicator indicates that the document is: Accept and continue Learn more about the cookies we use and how to change your settings.
This section deals only with a straight run of conductor. The total electrode area formed by the underground metalwork of large structure may often be used to provide an earth resistance lower then that obtainable by other methods.
The standard gor relevant in the following sectors: Take the smart route to manage medical device compliance.
They may be used to give an indication of the difficulties that one might face in preparing an adequate design at the chosen location. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3. Foundation metalwork in concrete may be used as a bs 7430 code of practice for earthing made and effective earth electrode.
Manish Darji Feb 26, It may be considered necessary to apply numerical methods which are more complex than the formulae given below and software is available to carry out the more detailed calculations. The Amber document status indicator indicates that some caution is needed when using this document – it is either: Therefore, the various factors which affect the resistance to earth and fault current capacity of the buried conductor, designated the earth electrode, should be considered.
In particular, continuous earth currents should be given attention. Soil resistivity may be measured in a similar manner to the establishment of the resistance of the earth electrode.
The effect of other reinforcement which might be attached by wire ties only, may be neglected. Second edition, November Premium Membership Premium membership gives you an access to specialized technical articles and extra premium content electrical guides and software. The value of resistance required might not always be amenable to an automatically set value. Care should be taken to avoid a site where water bs 7430 code of practice for earthing over it e.
The connecting strip to the above ground disconnection point should be fully insulated to avoid electrolytic action. It provides recommendations and guidance on meeting the requirements for earthing land-based electrical bs 7430 code of practice for earthing in and around buildings in the UK. This should include the size and shape of the earth conductor, the resistivity of the soil in which it is buried and the connection of the system to it.
Alternating current should not be expected to cause corrosion, but, rectification sufficient to produce a very small proportion of direct current might take place. The faster, easier way to work with standards.